SCADA System Evaluation and Upgrade
Client: Coldwater Board of Public Utilities
Location: Coldwater, Michigan
Coldwater Board of Public Utilities operates and maintains the Water and Wastewater Treatment Facilities including the Water Treatment Plant, two booster pump stations, three water towers, a Wastewater Treatment Plant, and fourteen wastewater lift stations. There were existing control systems in place to aid in the operation of these facilities, however, the existing control systems throughout the facilities were not standardized and, in some cases, were past their intended (or supported) life span.SCADA System Path Forward Study
It was Coldwater’s goal and Donohue’s recommendation to standardize the control system throughout the facilities. The recommended standardization includes, but is not limited to, hardware, software, communication, graphical displays, alarming, equipment functions, logic functions, and historical data collection and compression. There are numerous benefits to having a standardized control system. Increased reliability, reduced overhead costs, and more effective operations are a few of the key benefits that were realized upon completion.SCADA System Upgrade
Based on the SCADA Path Forward Study, Donohue provided various hardware, systems integration, and programming improvements. The Water Plant’s existing SCADA software licensing was upgraded to be utilized for the entire utility. By combining the SCADA system into one application rather than two, the Utility saved approximately $100,000 as well as annual maintenance and support fees of $20,000 per year. The SCADA system was installed on four virtual servers in coordination with the CBPU IT Department. Virtualization allows for reduced server hardware cost, and regular “snapshot” backups of servers for disaster recovery.
Standardized PLC programming and SCADA graphics were developed for consistency throughout the utility for easy maintenance and troubleshooting in the future. Obsolete control hardware was replaced and new PLC hardware provided a distributed approach, where each process area has its own controller. Controllers throughout the plant communicate to each other on a limited basis, but are not completely reliant on each other to run the process. Networking upgrades provide a faster, more robust, Ethernet network through the plant.